RPM Digital Print Ltd – LED installation & boiler replacement
Project cost: £5,186
Estimated savings: 5 tonnes of CO2 / over £900 per year
Equipment / installer: 39 LED Lights (Low Energy Solutions) / Worcester Bosch Greenstar 29 CDi classic boiler (GWE)
The project: RPM Digital is a print and digital marketing company based in Wimborne, Dorset. In an effort to reduce their consumption of electricity and gas, RPM upgraded lighting throughout their offices to LEDs, and replaced an aging inefficient gas-combi boiler with a highly efficient condensing gas boiler.
Getting started: With an environmental management system already in place, RPM Digital base their business practices on working in an ethical and sustainable way. Aware that their premises were not as energy-efficient as they could be, but restricted by the costs of upgrading equipment, RPM contacted Low Carbon Dorset for support.
An initial energy report carried out by Low Carbon Dorset’s technical officer Erik, highlighted the carbon and cost savings that could be made from upgrading RPM’s lighting and gas-combi boiler. Within the report, alongside the recommended changes and potential savings, Erik outlined the likely cost of the project and payback periods.
With this information at hand RPM were able to plan their carbon reduction project according to their requirements and budget.
LED Lighting: 59 existing lights, mostly fluorescent tubes consisting of quadruple 18W, single 58W, or double 58W T8 fittings, were replaced with 39 highly efficient LED lights. Several of the existing lights were daylight tubes to help with quality control in the print works. These lights were replaced with LED daylight tubes. The replacement of the lights alone will make an estimated annual saving of 2.4 tonnes of CO2 / £600.
Boiler upgrade: Hot water and heating was previously supplied to the offices through a gas combi-boiler. This non-condensing boiler had a SEDBUK (Seasonal Efficiency of Domestic Boilers in the UK) efficiency rating of under 79%. By making a simple switch to a 90%+ efficient condensing gas boiler RPM will make savings on energy use and bills. These savings are estimated at 2.6 tonnes of CO2 and over £300 per year.
Other recommendations: Further recommendations made in the RPM Digital energy report included more investigation into the barriers for installing Solar PV on the factory roof. And a detailed assessment of the building’s heating, ventilation, and air conditioning (HVAC) system by a HVAC engineer to identify potential energy and carbon savings. RPM Digital can apply for further grants from Low Carbon Dorset to carry out these recommendations until the programme ends in 2020.
- Date January 4, 2019